Open today from 8am - 9pm
0203 763 2682
Gas Safe Register is the official gas registration body for the UK, Isle of Man and Guernsey, appointed by the relevant Health and Safety Authority for each area. By law all gas engineers must be on the Gas Safe Register.
Visit the Gas Safe website to verify our accreditation
We operate to the highest standards, that’s why we’re endorsed as a Which? Trusted Trader.
Your boiler's pressure is usually displayed on the boiler's built-in pressure gauge, and should read around the 1 bar mark when you are not running any hot water and the central heating is not turned on. Therefore, 1 bar is a low-pressure setting.
Once the boiler begins to heat water, the heated water expands and causes the pressure gauge to increase. With an in-built pressure relief valve, boilers are well-set to control these quick leaps in pressure so you don’t need to worry if the boiler shows an higher pressure than you expected when you are both using the central heating and running hot water. Once you have finished using the heating and hot water, the pressure should lower back to safe levels almost immediately.
If your boiler pressure still persists to be too high, there could be one of two issues; Either you may need to re-pressurise the expansion vessel, or you could have a fault with the filling loop. However, you will not be able to do this yourself and will need to call a Gas Safe engineer. Even though the pressure may still be irregular, the pressure relief valve should prevent the boiler from overpressurising so you will still be safe to carry on as usual as long as you are not experiencing loud, unusual noises coming your boiler and your boiler is still functioning properly.
Your boiler pressure is too low if your pressure gauge is showing that your boiler pressure is below the 1 bar mark. It’s important that you increase the boiler pressure to its normal state as soon as possible.
The boiler must be switched off and completely cool before starting to re-pressurise.
To increase the boiler pressure, you will need to find the filling loop. This is a flexible hose found underneath your boiler with a small valve at each end. Then make sure both ends of the hose are secure and tightly attached to the two valves.
By using a flat headed screwdriver, you can open the valves by their tap handles. This will then allow the cold mains water into the system, you should hear this filling up the system.
The pressure will then increase so keep a close eye on the pressure gauge until it reaches a 1.5 bar mark; you can then close off both valves, one at a time. As your boiler is now at the desired pressure, feel free to switch the boiler back on, and follow by resetting the boiler.
If you still have any concerns regarding your boiler pressure, get in touch with our experts on 0203 805 4581 .
We’re all about the personal touch, so fill in the form below to give us an idea of where you are and one of our local advisors will give you a call back quick-sharp.
If you know exactly what you‘re after, call the number below
0203 805 4581
Chat to one of our customer service champions now with our live chat systemChat now
 Exclusions apply. See www.help-link.co.uk/fixed-price-quote-faqs/
Help-Link UK Ltd is authorised and regulated in the UK by the Financial Conduct Authority FRN 689798 for credit broking activities
Help-Link UK Ltd, 3310 Century Way, Thorpe Park, Leeds, LS15 8ZB | VAT Number: GB 277 8107 71. Company Reg: 03527087
© Help-Link UK Ltd 2018